In plumbing water systems (PWSs), there are two main layouts for water pipe networks (WPNs) within buildings: branched and looped layouts. The aim of this study is to introduce an approach for improving the performance of PWSs using looped water pipe networks within buildings. This approach is applied to a case study of branched configuration that is firstly changed to a looped configuration with the same pipe diameters, secondly to a looped configuration with the same discharge and velocity, and thirdly to the same branched configuration with double the pipe diameters. All cases were analyzed for cost and hydraulic reliability in terms of resilience index, minimum surplus head, failure index and demand node's flow path. EPANET software was used for hydraulic analysis of all cases. It is concluded from this study that replacing branched configuration of PWSs by looped configuration improves the hydraulic reliability and minimizes the costs of the PWSs.
Water pipe networks (WPNs) supply water from a water source or water treatment plant to the consumer's water service pipe. Plumbing water systems (PWSs) run from the water service pipe to all interior plumbing fixtures in the building. Both WPNs and PWSs can be defined as groups of multiple interconnected components (pipes, fittings, valves, etc.) arranged in different layouts and configurations. Branched and looped configurations are the main layouts for WPNs and the first is commonly used for PWSs within buildings.
While branched layouts are quite simple and have acceptable investment costs, they have low reliability, which affects all consumers located downstream of any breakdown in the pipe system, and fluctuating water demand that results in large pressure variations. This is different in looped layouts, where consumers can be supplied following many paths.
Mechanical failure can be described as system failure due to pipe breakage, pump failure, and power outages, etc. Using the troubleshooting manual for detecting, identifying, studying and solving the problems that occur in a water distribution system is essential to avoid the mechanical failure of the system and reduce the annual maintenance cost (Kanakoudis 2004a, 2004b).
Hydraulic failure can be described as system failure due to inadequate distributed flow and pressure head at one or more demand nodes. System reliability means keeping a constantly open path between the demand nodes and the supply nodes. For each demand node, these paths are independent (Kanakoudis & Tolikas 2002a; Metin 2003).
Looped layouts improve the hydraulic reliability of the pipe systems. This is very important, especially whenever a supply pipe is out of order due to cleaning or repairs (Trifunović 2002). While looped layouts are expensive and more complex to design than branched ones, the higher reliability of the looped layouts can compensate for the increase in their costs (Banosa et al. 2009).
Hydraulic reliability is an indicator of the performance of the water pipe network. It can be defined as the ability of the network to sufficiently meet water demands at adequate pressures. The estimation of hydraulic reliability for the water distribution network is subject to uncertainty due to variations in future water demand, required pressure heads, and pipe roughness (Bao & Mays 1990).
In 1977 Kapur and Lamberson were the first to calculate the hydraulic reliability of a network, when its different parts are placed in series or in parallel, using the Kapur and Lamberson equations. In 2003 Prasad et al. used genetic algorithm methods and introduced ‘network resilience’ as a new reliability index. Kanakoudis & Tsitsifli (2011) proved that the Discriminant Analysis and Classification (DAC) method is a useful tool for evaluating a water pipe network's reliability considering all pipe characteristics. Kanakoudis et al. introduced a new methodology concerning the hierarchical analysis of the protective maintenance actions in WPNs considering repair or replacement cost and the possible failure impacts to satisfy demand using alternative paths. Kanakoudis et al. presented a simulation cost-based optimization and risk analysis process using the Pipe 2000 and the EPA net codes, aiming for the minimum operating cost (Kanakoudis & Tolikas 2002a, 2002b, 2002c; Kanakoudis 2004a, 2004b; Kanakoudis & Tsitsifli 2011; Tsitsifli et al. 2011).
The aim of this study is to present an approach for improving the performance of plumbing systems using looped configuration layouts instead of branched ones, which increases the hydraulic reliability and minimizes the costs of the system. This approach was applied to a case study (Harris 1990) of a branched layout configuration as a reference. The case study configuration is changed three times to examine the reliability and corresponding costs for each variation. It may first be changed to a looped layout with the same pipe diameters (Loop I), secondly to a looped layout with the same flow and velocity (Loop II), and thirdly to the same case study configuration with double the pipe diameters (Harris 2D).
The above cases were analyzed for costs and hydraulic reliability in terms of resilience index, minimum surplus head, failure index and demand node's flow path. An EPANET hydraulic simulator was used for the hydraulic analysis of all cases. The head-dependent analysis (HDA) approach was applied, which provides even more realistic results when the case study system operates under subnormal pressure conditions.
Nodal head and pipe flow velocity constraints
Pipe size availability constraints
Demand node flow path constraints
HYDRAULIC RELIABILITY EVALUATIONS
Penalized objective function
Resilience index (Ir)
Minimum surplus head (Im)
Failure index (If)
Reference example of Harris branched configuration (Harris)
Harris (1990) provides an example of a typical plumbing water distribution system of a one-family residential home. Figure 1 represents a schematic based on Harris's example (Harris 1990). The street main is assumed to provide daily service pressure of 50 psi (344.7379 kPa) as in Harris (1990). The system includes fixture groups located on three floors (basement, first floor, and second floor). Cold water pipes are designated by solid blue lines with cold water demand nodes Q, E, J, and K on the basement floor; M on the first floor; and O and P on the second floor. Hot water pipes are designated by dashed red lines with hot water demand nodes C’ and F’ on the basement floor; H’ on the first floor; and J’ and K’ on the second floor.
A worst-case loading scenario upon the system with all fixtures operated simultaneously was introduced. Although this situation is not realistic, it does provide a basis for analyzing the behavior of the system (Ladd 2005). An EPANET hydraulic simulator program was used for hydraulic analysis of Harris's example plumbing water network and the other looped and branched cases explained below.
Conceptual looped configuration (Loop I)
Harris branched configuration double supply pipe diameter (Harris 2D)
Conceptual looped configuration (Loop II)
RESULTS AND DISCUSSION
Table 1 shows the values of , , and for the four configurations considered in this study for the three floors: basement, first floor, and second floor.
|Basement .||First .||Second .||Basement .||First .||Second .||Basement .||First .||Second .|
|Basement .||First .||Second .||Basement .||First .||Second .||Basement .||First .||Second .|
Resilience index (Ir)
Figure 3 represents comparisons of resilience index values for the three floors among the four alternative configurations: Harris, Loop I, Loop II, and Harris 2D. It is clear from this figure that, for the three floors, the value of resilience index is highest for the Harris 2D configuration and lowest for the Loop I configuration. In addition, it is observed that the Loop II configuration results in better than that of Harris.
Minimum surplus head
Figure 4 represents comparisons of minimum surplus head values for the three floors with the four alternative layouts: Harris, Loop I, Loop II, and Harris 2D. It is clear from this figure that, for the three floors, the value of is highest for the Harris 2D configuration and lowest for the Loop I configuration and has a negative value on the second floor which means that the pressure head at the demand nodes on this floor are lower than the desired head to meet the demand. The layout of the Harris 2D provides the maximum performance with the highest value of and Loop I configuration provides the minimum performance with the lowest value of . In addition, the Loop II configuration provides better performance than the Harris configuration.
Figure 5 represents the variations of the failure index values for the three floors with the four alternative models of Harris, Loop I, Loop II, and Harris 2D. It is clear from this figure that values of vanish for the basement and first floor. On the second floor the value of is highest for the Loop I configuration and lowest for the Harris 2D configuration. Loop I configuration reflects the worst performance, accompanied by the biggest value of . In addition, it is observed that the Harris 2D configuration results in better than that of Harris.
Figure 6 shows variations of the different cost functions, the actual cost , the cost related to the hydraulic constraints , the cost related to the number of independent flow routes to the demand joint , and the total cost function for the four alternative models Harris, Loop I, Loop II and Harris 2D.
It is clear from the figure that the values of actual costs of both Harris and Loop I configurations are smaller than those for Loop II and Harris 2D configurations. The values of costs related to the hydraulic constraints of Harris, Loop I and Harris 2D configurations are smaller than that of the Loop II configuration.
Similarly for the cost related to the number of independent flow routes to demand joints Loop I and Loop II configurations entail much lower costs than the Harris and Harris 2D configurations. The value of the total cost function is lowest for the Loop I configuration followed by the Loop II configuration with a little higher cost.
An approach for improving the performance of PWSs using looped WPNs within buildings is introduced in the present study. This approach is applied to a case study of branched layout configuration which was changed to a looped configuration with different pipe diameters and velocities. All cases were analyzed for cost and reliability, in terms of resilience index, minimum surplus head, failure index, and demand node's flow path using EPANET software. It is concluded from this study that using a looped configuration for PWSs inside buildings greatly improves the performance of the system since the overall hydraulic reliability of the system is increased in terms of resilience index, minimum surplus head, failure index and demand node's flow path. Using a looped configuration for PWSs inside buildings also decreases the pressure variation at plumbing fixtures, supplying sufficient demand at each of them since every demand node has many demand paths that do not affect each other which provides a good service to householders.
In addition, using a looped configuration for PWSs inside buildings minimizes the total cost function of the system which is the summation of actual cost, cost related to the hydraulic constraints and the cost related to the number of independent flow paths to demand nodes.