Conventionally, the design of urban water supply and distribution systems is based on the assumption that all the involved parameters are known a priori and remain unaltered throughout the life cycle of the system. However, significant uncertainties do appear during the analysis and design of these systems, such as the equivalent pipe roughness and the actual internal diameters of the pipes. To study these uncertainties, the water supply and the looped water distribution systems are studied separately. For the water supply system, these uncertainties are incorporated in the analysis of the system, using the extension principle of the fuzzy sets and a new operation of the fuzzy subtraction. Based on the calculation of head losses for each branch of the system, the nodal heads are obtained as fuzzy numbers. In regard to the looped water distribution system, a methodology is developed and proposed, based on the extension principle and leading to several optimisation problems with respect to the branches of the system. The aim of the proposed methodology is to determine the α-cuts and finally produce the shape of the membership function of flows in the branches of the system. Both methodologies are illustrated by numerical examples.
INTRODUCTION AND BASIC NOTIONS
It is commonly accepted that the urban water supply system is a branched pipe system, whereas the distribution systems are looped pipe systems. During the design stage, it is customary to analyse both systems based on the assumption that all the involved parameters are known or can be calculated at the design stage, and remain unchanged throughout the life cycle of the facility.
However, most of the involved parameters are accompanied by uncertainties which cannot be neglected at the design stage. Indeed, the real conditions of ‘running’ water supply systems differ greatly from theoretical considerations for a variety of reasons, such as financial shortcuts (Kanakoudis 2004), the ravages of time, the uncertainty in the maximum water consumption, etc. Among the parameters exhibiting uncertainty are the pipe roughness, the internal pipe diameter and the required water flow through each branch of the system (Spiliotis & Tsakiris 2012; Tsakiris & Tsakiris 2012). To deal with these uncertainties, two cases are studied separately: the branched water supply system and the looped water distribution system.
A number of methodologies dealing with the uncertainties of these parameters exist in the related literature (Xu & Goulter 1998; Xu et al. 2003; Giustolisi et al. 2009; Alvisi & Franchini 2010). The uncertainties studied by Xu & Goulter (1998) and Xu et al. (2003) are restricted to small deviations from the mean, since they are based on the development of Taylor series around the mean values.
This paper deals with all these uncertainties using two innovative, ‘low data demand’ methodologies based on fuzzy sets and logic. In addition, the proposed methodologies can cover a wider range of values around the mean values. Before presenting the proposed methodologies, it is wise to briefly summarise some of the most basic principles of the analysis of the water supply and distribution systems.
In the case of a branched pipe water system, since the flow at each branch can be considered known, the head at each node, H, can be determined directly from the head of the previous node by subtracting the head losses of the branch connecting the two nodes.
The uncertainty in the branched water supply systems has been recently studied also in Tsakiris & Spiliotis (2016).
Regarding the looped pipe systems, most often encountered in municipal water distribution systems, there is an extra complication since we cannot predict the direction of the flow. Furthermore, when examining the maximum flow at a branch, then larger values of the pipe roughness coefficient for a water path should be combined with smaller values of the pipe roughness coefficient for another water path. The unknown distribution of flows and the complicated interaction between the several variables of the looped pipe systems makes the fuzzy analysis in this case more difficult and complicated.
This paper focuses on the uncertainty encountered in a looped water distribution system assuming that the internal diameters and the pipe roughness coefficients are not crisp numbers, as conventionally thought. In addition the authors extend the methodology of Revelli & Ridolfi (2002), who suggested a fuzzy approach for the analysis of a pipe system considering uncertain parameters of looped pipe system based on Q-equations. An innovative aspect of the modification is the use of α-cuts instead of the direct use of the membership functions of the corresponding fuzzy sets. In fact, the optimisation procedure is used in order to determine the fuzzy output quantities (i.e., flows) from a system with crisp Q-equations, while some variables are fuzzy numbers. In this article, the pipe roughness coefficients and the internal diameters are expressed as fuzzy quantities. In contrast, the method presented by Spiliotis & Tsakiris (2012) analysed the uncertainty based on fuzzy water consumption at the nodes.
The uncertainty on internal diameters stems from the fact that due to deposition of material in the pipes over the years, the effective diameters of the pipes are getting smaller.
Finally, in this article, a global objective function is proposed with the aim to reduce the fuzziness and simplify the computational process. The global objective function takes into account all the branches of the system.
A fuzzy number is a fuzzy set satisfying the properties of convexity and normality. It is defined in the axis of real numbers and its membership function is a piecewise continuous function. A simple fuzzy number for representing the water demand at the node n is a fuzzy triangular number.
In the case of a fuzzy triangular number, its α-cut, , is the following (crip) set:
We can now extend the operation of the usual crisp functions, if the inputs are fuzzy sets, based on the extension principle, which is briefly presented below.
where are the α-cuts for the fuzzy parameters x1, x2 and x3, respectively.
From the theorem of global existence for maxima and minima of functions with many variables, it is known that if the domain of a real function is closed and bounded and the real function is continuous, then the function will have its absolute minimum and maximum values at some points in the domain (Marsden & Tromba 2003; Tsakiris & Spiliotis 2014). Based on this theorem, it is evident that the α-cut for any real continuous function with real variables in this domain can be determined, given that the inputs are fuzzy triangular numbers.
FUZZY ARITHMETIC OPERATION AND A NEW FUZZY ALGEBRA
METHODOLOGY FOR WATER SUPPLY SYSTEMS
The basic idea is that for every branch of the water conveyance system, we calculate the head losses based on the extension principle and, thus, we take into account all the associated uncertainties. The effective internal diameter, the equivalent roughness and the discharge are considered as fuzzy triangular numbers based on the experience of the professionals. Therefore, based on our experience, the left- and the right-hand sides of the zero-cut for a fuzzy number can be estimated. In addition, in contrast to the interval or the grey systems approach (e.g., Alvisi & Franchini 2010), a central value can be supposed. To understand the concept of central value, the used fuzzy number can be named as ‘around the central value’. On the contrary, in the case of the probabilistic approach, a historical sample is required and not only the extremes and the central value. By taking into account all the α-cuts of the parameters an optimisation problem should be solved. Further, according to the extension principle (selection of several α-cuts), the membership function of the head losses can be determined.
In Equation (19), ν = kinematic viscosity of water (m2/s); kin = pipe roughness coefficient (m); Din = internal diameter of the branch in (m); Lin = length of the branch in (m).
It should be clarified that the minor losses are included in the linear losses by following an indirect way according to the Greek experience, that is, by increasing the pipe roughness. This practice can be found also in other countries, especially when we deal with water distribution networks.
Since the head losses of each branch have a non-linear mode, non-linear membership functions for the nodal heads are expected.
METHODOLOGY FOR WATER DISTRIBUTION SYSTEMS
As mentioned previously, the use of the α-cut instead of the membership function of the corresponding fuzzy sets is adopted. The analysis is based on the crisp Q-equations, whereas the fuzzy inputs are the α-cut sets for the pipe roughness coefficients and the internal diameters. However, it should be stressed that for each optimisation problem, the decision variable x1,in, which corresponds to the flow at branch in, takes only crisp values.
In contrast with the water supply system, the analysis of looped distribution systems involves all the branches of the system simultaneously, since it is not possible to deal with the head losses of each branch separately.
In addition, in this work, a new method is proposed to produce a simultaneous estimation of all hydraulic variables and their fuzziness. The aim of this method is to reduce the fuzziness and simplify the computational process based on a global objective function; that is, to use a function which involves all the branches of the system. Therefore, an objective function which comprises the weighted sum of the absolute values of the head losses is proposed. The selection of the weights is based on the principle that each weight is directly proportional to the corresponding flow:
We should confess that by using the global objective function, we do not capture the entire range of fuzziness as in the previous two methods. However, the global optimisation method leads to the reasonable conclusion that the most unfavourable values for the pipe roughness, internal diameters and water consumptions will take place almost simultaneously.
CASE STUDY FOR THE WATER SUPPLY SYSTEM
In this section, a simple water supply system with third-generation PE pipes is studied for illustrating the use of the proposed methodology (Figure 2). The internal diameter, the length and the flow of each branch are depicted in Table 1. We assume that the fuzzy numbers representing the pipe roughness, the internal diameter and the flow can be described as follows: (a) pipe roughness coefficient, k: 0.45, 0.50, 0.60 (mm); (b) internal diameter, D: D−4, D, D+2 (mm), if D>200 (mm), D − 2, D, D+1 (mm), if D≤200 (mm); (c) design flow, Q: 0.95Q, Q, 1.05Q (L/s). The first and the third values are the left-hand and the right-hand boundary of the 0-cut, whereas the second value denotes the central value of each fuzzy set. Fuzzy triangular numbers are adopted for all the above parameters.
|Main branches||Length, L (m)||Internal diameter, D (mm)||Flow, Q (L/s)|
|Main branches||Length, L (m)||Internal diameter, D (mm)||Flow, Q (L/s)|
In brief, the nodal heads can be calculated following the steps below:
The fuzzy parameters (e.g., k, D) of the water supply system are expressed as fuzzy triangular numbers. In the case of the fuzzy flow at the main branches of the water supply system, the authors apply the modified fuzzy subtraction as explained above (Equation (16), Figure 3).
The head losses through each branch are calculated individually based on the extension principle (Equation (18)) for a significant number of α-cuts.
Going from upstream to downstream and by following the water flow direction, the hydraulic head at each node is calculated based on the conventional fuzzy subtraction of Equation (16). The results are shown in Figure 4.
It is observed that by applying the proposed method for increased fuzziness of water flow, e.g., higher than ±5% of the initial flow, the membership function of the head at the nodes loses its linear shape.
It can also be concluded that the pipe roughness is a critical and sensitive parameter in relation to the fuzziness of the final results. To show the importance of the uncertainty of pipe roughness towards the fuzziness of the nodal heads, the nodal heads are calculated keeping only the uncertainty of the pipe roughness. The results of this calculation are presented in Figure 5 for comparison purposes.
Finally, a critical point in this analysis is associated with the initially selected diameters. In the case where smaller diameters are selected and therefore high velocities produced, the fuzziness of the final results is significantly increased.
NUMERICAL EXAMPLE FOR THE LOOPED DISTRIBUTION SYSTEMS
The system, presented in Figure 6, consists of two loops, five branches and four nodes. The examined system is the system presented by Revelli & Ridolfi (2002), slightly modified. Larger diameters have been selected to fulfil the constraints of maximum allowable velocity. The Hazen–Williams equation is used for the calculation of head losses. Furthermore, the uncertainty in this example refers not only to the pipe roughness coefficients (as in the original paper), but also to the internal pipe diameters. Indicatively, Figure 7 presents the fuzzy inputs for the pipe roughness coefficient and the internal diameter of the branch 1–3.
Following the Revelli and Ridolfi methodology, the separate solution for the maximum or minimum flow at each branch for several α-cuts, provides the corresponding α-cut of the flow at each branch and finally the shape of each membership function. In Figure 8, the membership function of the flow of the branch 1–2 is presented. This process must be repeated for every branch and simultaneously for a discrete number of α-cuts.
Thus, the left-hand boundary of the flow at branch 1–2 is equal to . Based on the optimisation results, branches 1–3, 3–4, 3–2 have Hazen–Williams coefficients near the lower boundary, whereas the branches 1–2 and 2–4 lead to Hazen–Williams coefficients near to the upper boundary to facilitate the water path (1 → 2 → 4). The same behaviour is obtained considering the values of the internal diameters.
Indicatively, Figure 9 presents the head losses at branch 1–2 based on the minimisation and maximisation of flow at branch 1–2, whereas Figure 10 presents the same varieties based on the minimisation and maximisation of the head losses at branch 1–2. By comparing the two solutions it is obvious that they are not the same. Equation (24) leads to a larger support of the head loss fuzzy number than Equation (23). This is clearly due to the fact that in Equation (24) minimum and maximum head losses are explicitly searched for, but it could also be due to the combined effect of fuzzified roughness and internal diameter.
Another interesting point of view is that in the case of Equation (23), if we consider fuzziness only in pipe roughness, then, the flow at pipes 1–2 will have the same central value but with less uncertainty (without dramatic reduction) compared with the case where uncertainty exists both regarding the pipe roughness and the internal diameters (Figure 8).
In contrast with the individual maximisation of the flow at each branch, by using the proposed global objective function, we derive a solution which consists of the left-hand boundary of both the pipe roughness coefficients and the internal diameters.
Subsequently, the proposed global objective function is dealt with in order to cover the case of variable demand at nodes. The water consumption at nodes is expressed as fuzzy triangular numbers. A symmetrical semi-width of 10% around the central value is assumed. The results are presented in Figure 12. Since in this case the authors consider fuzzy consumption at nodes, the fuzziness (i.e., the length of the 0-cuts for the water flow at branches) is increased (Figure 12).
By comparing the fuzziness produced from the examples of both the water supply and the looped distribution systems, it can be deduced that the water supply system produces higher output fuzziness due to anticipated significantly greater pipe lengths involved. Also, the proposed methodology of the global optimisation of the weighted sum of the head losses at branches, leads to a more condensed subset of fuzziness, convenient for operational use.
In this paper, an attempt is made to study the branched water supply and looped water distribution systems. The uncertainty of the variables involved (as the internal diameter of the pipes, the water consumption and the pipe roughness) is taken into account. In this context, innovative methodologies are developed and proposed for each type of system, separately. The proposed methodologies use a small number of data in comparison to existing ones, such as the probabilistic methods, found in the scientific literature.
The methodology developed for the analysis of branched water supply systems comprises the extension principle of fuzzy sets and new operations of fuzzy algebra. Based on the results, it can be concluded that this methodology leads to useful recommendations for the design of these systems, provided that the water velocities are kept at a medium or low level. It is also concluded that the pipe roughness coefficient is a critical parameter in the analysis, imposing significant fuzziness on the head losses at the branches and on the nodal heads.
For the analysis of the looped distribution systems under uncertainty, two methodologies are developed. In both methodologies, the fuzzy inputs are from the pipe roughness coefficients and the internal diameters. The first methodology is based on a modification of Revelli and Ridolfi's approach by determining the α-cuts and finally the membership functions of the flow at the branches. This is achieved by following an optimisation approach. The second methodology refers to a global optimisation function involving all branches simultaneously, which results in identifying a condensed subset of fuzziness which is, however, convenient for operational use.